Surface temperature survey showed that the reboiler condensate was highly subcooled. Analysis in terms of vapor pressure led to the conclusion that due to the subcooled liquid, the condensate drum did not operate like a normal drum with a normal vapor space. This explained why the liquid level was insensitive to the level valve opening. The hammering was due to the collapse of steam onto the subcooled condensate.
The problem was solved by restoring vapor space to the drum. This was achieved by relocating the condensate entry below the liquid level and adding a channel baffle to keep the subcooled condensate away from the drum liquid surface. The level measurement was modified to measure the level across the drum only and not both the drum and reboiler. Following the modifications, the hammering was entirely eliminated and good automatic level control was established.
Lessons learnt are that correct, inexpensive hydraulic design of a condensate pot is central to stable, trouble-free reboiler operation, and that contrary to recent published reports, correctly locating the condensate inlet to the drum is central to trouble-free operation.
Would you like to access this content?
No problem. You just have to complete the following steps.
You have completed 0 of 2 steps.
You must be logged in to view this content. Log in now.
Purchase Technical Presentation
You must purchase this technical presentation using one of the options below.
If you already purchased this content recently, please click here to refresh the system's record of ownerships.
|Credits||0.5 Use credits|
|List Price||$25.00 Buy now|
|AIChE Members||$15.00 Buy now|
|AIChE Undergraduate Student Members||Free Free access|
|AIChE Graduate Student Members||Free Free access|