Several changes were made as a result of a multi-disciplined member team root cause investigation. The site has recently performed a turnaround during which follow up inspections were made to evaluate the system changes. The purpose of this paper is to describe damages found, to review the evaluation of the changes implemented, and share additional recommended actions for improvement. This experience offers a basis for establishing best practices considering time and service expectations of cooling water system exchangers.
Would you like to access this content?
No problem. You just have to complete the following steps.
You have completed 0 of 2 steps.
You must be logged in to view this content. Log in now.
Purchase Technical Presentation
You must purchase this technical presentation using one of the options below.
If you already purchased this content recently, please click here to refresh the system's record of ownerships.
|Credits||0.5 Use credits|
|List Price||$25.00 Buy now|
|AIChE Members||$15.00 Buy now|
|AIChE Fuels and Petrochemicals Division Members||Free Free access|
|AIChE Undergraduate Student Members||Free Free access|
|AIChE Graduate Student Members||Free Free access|